# Circuit Breaker Selection of LT and HT Side | Circuit Breaker Calculations

There are some circuit breaker calculations for the circuit breaker selection on the LT and HT side. We have already published a lot of articles about circuit breakers on this blog.

There is no need for calculation for the circuit breaker selection of the HT section and it is very easy to select, but it is necessary to calculate the circuit breaker selection on the LT side.

• HT Side Is used.
• LT Side  A  ACB, MCB, MCCB, Etc. are used.

## The Breakers Available in the Market

#### VCB

 Serial Rated Current (A) Breaking Capacity (KA) 1 630 25 2 1250 40

#### ACB

 Serial Rated Current (A) Breaking Capacity (KA) 1 630 85 2 800 85 3 1000 85 4 1250 85 5 1600 85 6 2000 85 7 2500 100 8 3200 100 9 4000 100 10 5000 100 11 6300 150

 Serial Rated Current (A) Breaking Capacity (KA) 1 40, 43, 100 & 125 25 2 160, 200 & 250 25 3 250 25 4 320 & 400 65 5 500 65 6 630 85 7 800 85 8 1000 100 9 1250 100 10 1600 65

### Circuit breaker calculations in high tension (circuit breaker calculations)

33 KV to 11 KV  In the case of transformers 1250A Ratings VCB  Is selected and 11 KV to 0.4 KV  In the case 630A  Ratings VCB Is selected. Below is the latest one  0.4 KV Low tension is associated with side, low tension is connected VCB That’s it 630 A The rating is VCB Have to choose

• HT section A 1250 A VCB
• HT Section Associated with its LT section On top of that 630 A VCB Is selected.

Notice the image below:

In the figure above  5 MVA, A step-down transformer of rating has been used. In its primary  33 KV The line enters the secondary 11 KV  Has come out This is a high tension section where 1250 A  The rating is VCB Has been used.

In the figure above 2500 KVA, A transformer of rating has been used. In its primary 11 KV  Entered and into the secondary 0.4 KV Got out That is, its primary section HT, The secondary section of it LT. HT  From the section LT The section is connected via a transformer, in this case, the upper HT Section VCB Will be 630A The rating is.

## LT Side Breaker Selection (Circuit Breaker Calculations)

Circuit breaker selection requires a little more current than the line current, or the circuit breaker selection of the current quality.

### Breaker 1 Selection

We need to calculate the value of the transformer above the breaker 1.

P = 2500 KVA

V2 (Secondary) = 0.4 KV

I = ?

Notice one thing from the image above, 2500 KVA There is no resistive, inductive, capacitive load on the transformer. Do you remember the power factor in this case ???

Apparent Power, P = √3 V I (KVA)

Active Power, P = √3 V I Cosθ (KW)

Re-Active Power, P = √3 V I Sinθ (KVAR)

Guess which formula to use ????

Sure  P = √3 V I Because 2500 KVA There is no active power and reactive power in the line from above. In that case, what will be transmitted from the grid is what we get.

Then I = P / √3 V

I = (2500 * 10^3) / √3 * 0.4 * 10^3

I = 3608.43 A

Then select the circuit breaker 3608  A Or maybe a little more around. Directly 3608 A Circuit breakers are not available in the market. Now look at the market above the table

Then from the chart above 3608 A  For that we 4000 The rating is ACB I can use a circuit breaker.

## BREAKER 2 & 3 SELECTION

Notice the image above, obtained from the output of the transformer 3608 Empire but breaker for bus 2, 3, 4, 5, 5 It has been divided. In this case, the current must be calculated separately on each breaker. We need to know the power to find this current. Besides LT Voltage 0.4 KV We’ve already got it.

Breaker 2 and 3 Capacitor banks Are connected. This part provides reactive power. To get the power out Re-Active Power, P = √3 V I Sinθ (KVAR) Have to apply.

We know that in terms of power factor,

Cosθ = 0.8, Sinθ = 0.6

We already have, V = 0.4 KV, I = 3608 A

P = √3 V I Sinθ

P = √3 * 0.4 * 10^3 * 3608 * 0.6

P = 1499817 ≅ 15,00000

P = 1500 KVA

Breaker 2 and 3 There are two capacitor banks in the part where the power 750+750=1500 KVAR Can be used

Breaker 2 Power, in this case, P = 750 KVAR

I = P / √3 V

I = 750 * 10^3 / √3 * 0.4 * 10^3

I = 1082 A

This quality circuit breaker will not be available in the market. So ours from the chart ACB / MCCB 1250 A I can use anyone. ACB 1250 A It’s the tariff  MCCB 1250 A Much more than that So  MCCB 1250A Rating  We can select the unemployed.

Then the breaker 2 and 3 for this MCCB 1250A breaker selected.

### Breaker 4,5,6 Determine the power of the total load

Here you have to calculate the active power, whereV = 0.4 KV, I = 3608A, Cos θ = 0.8

Active Power, P = √3 V I Cosθ (KW)

P = 1999756 ≅ 2000000 W

P = 2000 KW

Then the breaker 4,5,6 Power of load in parts = 1000 + 500 + 500 Take it If you want 1000 +750+250 Can do with it.

### Breaker 4 Diagnosis

P = 1000 KW, V = 0.4 KV, I = ?

I = P / √3 V Cosθ

I = 1804 ≅ 1800 A

Breaker 4,5,6 As it is associated with the load, in accordance with international standards 20%Extra Breaker  Have to choose

Then: 1800 * 20% = 360

I = 1800 + 360

I = 2160 A

### The breaker of this Ampere rating is near 2500 A ACB. Then the breaker 4 for this 2500 A  Selected breaker of rating.

Breaker just like that 3 and 5 Have to choose And your comment on it. We will inform you by answering the answer. Be sure to comment if you have any questions about circuit breaker calculations.

### Owner Of ICEEET

Write more, thats all I have to say. Literally, it
seems as though you relied on the video to make your point.
You obviously know what youre talking about, why waste your intelligence on just posting videos to
your blog when you could be giving us something enlightening

Shivanand says:

Hello,
I red your article, While selecting a breaker, cant we consider its short circuit rating of breaker. beaker cost depends on the KA rating. please write how to select KA rating of the breaker.

We’re a group of volunteers and opening a new scheme in our community.
Your website provided us with valuable information to work on. You’ve done a formidable job
and our whole community will be thankful to you.

Have you ever thought about writing an e-book or guest authoring on other blogs?
I have a blog centered on the same ideas you discuss and
would really like to have you share some stories/information. I know my subscribers
would enjoy your work. If you’re even remotely interested, feel free
to shoot me an e-mail.

Yes, I’m very interested to work with you. Please feel free contact with me(Email- mjn.mijan@gmail.com). Thanks

In 2014, at tһe Whitｅ House Summit on Early Education, Aցe of ᒪearning ѵowed to the Purchase Us campaign to give
services vɑlued at greater than \$10 million to preschoоl, pre-k,
and Head Start class oνer 2 years.

It’s in reality a nice and useful piece of information. I’m satisfied that you simply shared
this useful info with us. Please stay us up to date like this.
Thanks for sharing.

At this time I am ready to doo my breakfast, when having my breakfast coming again to read other news.

Here is my blog post 3D Rendering

It’s perfect time to make some plans for the longer term and it is time to be happy.
I’ve learn this publish and if I may just I want to
recommend you few interesting things or advice.
I want to read more things approximately it!

I simply could not depart your website before suggesting that I really
loved the standard ijfo an individual supply to your visitors?

Is going to bee back often in order to inspect new posts

My site :: Elwood

This piece of writing is truly a good one it helps new web viewers, who are
wishing for blogging.

Feel free to surf to my web page: Phoenix search rankings

Wohderful beaqt ! I would like to apprentice while you amend your webb site, how could i subscribe for a blog
website? The account helped me a acceotable deal. I had been tiny bit acquainted of this your broadcast offered bright clear idea

Here is my blog … architectural renders

Hi there! This is kind of off topic but I need some help from
an established blog. Is it very hard to set up your own blog?
I’m not very techincal but I can figure
things out pretty fast. I’m thinking about setting
up my own but I’m not sure where to begin. Do you have any ideas or
suggestions? Many thanks

Valuable information. Lucky me I discovered your web site accidentally, and
I’m shocked why this twist of fate did not happened in advance!
I bookmarked it.

I am really inspired along with your writing skills as neatly
as with the structure on your weblog. Is this a paid subject or
did you customize it your self? Either way stay up the excellent quality writing, it’s rare to see a nice blog like this one today..

Here is my webpage non-owner policy

Nice replies in return of this matter with real arguments and telling all on the topic of
that.

Feel free to visit my website … auto accident

This paragraph is actually a pleasant one it assists new
internet people, who are wishing for blogging.

My family all the time say that I am killing my time here at net,
however I know I am getting knowledge daily by reading thes good content.

Hi there all, here every one is sharing these kinds of
know-how, therefore it’s pleasant to read this weblog, and I used to
visit this website daily.

A design like yours with a few simple adjustements would really make my blog shine.
a lot

Nice post. I learn something totally new and challenging on blogs I stumbleupon every day.
It’s always interesting to read through articles from other writers and use something
from other websites.

Just want to say your article is as astonishing. The clarity in your post is simply spectacular and i can assume you are an expert on this subject.
Fine with your permission let me to grab your feed to keep up to date with forthcoming post.
Thanks a million and please carry on the enjoyable work.

I’m now not certain where you are getting your information, but great topic.
I needs to spend a while learning more or working out more.
Thank you for wonderful information I was on the lookout for this information for my mission.

Heya! I just wanted to ask if you ever have any
problems with hackers? My last blog (wordpress)
was hacked and I ended up losing several weeks of hard work due to no data backup.
Do you have any methods to prevent hackers?